Smart energy monitoring systems are becoming increasingly popular these days to increase the energy efficiency of industries, buildings, etc. We have previously built an energy monitoring system to monitor power reading through a cloud server. But now we are going to build an Arduino-based smart energy monitoring system for AC current measurement. We have also seen AC current measurement multimeters from professional technicians which can measure current efficiently very efficiently. But these meters are so costly and also we can’t monitor the current all the time with this.
For this drawback, today in this project we are going to build an Arduino-based system that can detect current all the time, and display the result through an LCD display. And it is cost-effective. We are using CT (Current Transformer) sensor to measure current efficiently. This circuit also uses a rectifier and an amplifier for signal conditioning. For displaying the current we use a 16×2 LCD display. There are also many different ways to make this system like an Inductive sensor, Hall-Effect sensor, etc which we will discuss in another project. CT sensor can measure current range from 100mA to 100Amp.
- Arduino Nano
- SCT-013 CT Sensor
- LM358 Op-Amp
- 16×2 LCD Display
- I2C Display Module
- Resistor (10K, 22K, 1K)
- 100uF/25V Electrolyte Capacitor
- 1N5819 Schottky Diode
- 5 Volt Power Supply
Current Transformer for AC Current Measurement
The Current Transformer (CT) is a very safe method for measuring alternating current as there is no physical connection between the main AC current and the circuit. It is used in industries and large complexes where a large number of current needs to be measured. It is a type of “Instrument Transformer” that is made to produce an alternating current in its secondary winding coil which is proportional to the current being measured in its primary coil. Current Transformer reduces high voltage currents to a much minimal current and provides a convenient way of safely monitoring the actual electrical current flowing through an AC transmission line.
Unlike the voltage transformer, the Current Transformer consists of very few turns of the coil as its primary winding. This primary winding can be of either a single flat turn or just a conductor or bus bar placed through a central hole. There are three types of Current Transformers exist Wound Current Transformers, Toroidal Current Transformers, and Bar-type Current Transformers. In this project, we are using Toroidal Current Transformer.
SCT-013 Current Transformer Sensor
This is a Non-Invasive current sensor that has been used to sense the accuracy of the current measurement. SCT-013 is a split-core clamp-on CT sensor. Because of this feature, the CT has been clamped onto the single phase of the wire. In the output section, an AC voltage is engaged in direct proportion to the AC current change in the single phase.
Order PCB From PCBWay
There are so many forums or communities for electronics online in today’s technical world, and one of the famous ones for PCB manufacturing is PCBWay. PCBWay is a place that brings manufacturers and customers together. They have more than a decade of experience in this field of fabrication, prototyping and assembling PCBs. PCBWay has proved its focus on its customers’ needs in terms of cost-effectiveness, delivery, and quality.
How PCB Manufacturing Process Done in PCBWay
Standard quality for any product needs to be maintained using some parameters. PCBWay gives that opportunity through quality control in designing and manufacturing. At first, they ensure the accuracy, clarity, and validity of the PCB files that we sent to them.
Then all the boards will go through the most stringent tests other than the basic visual check. They adopt most of the testing and inspecting equipment used in the industry, such as Flying Probe Testers, X-Ray Inspection Machines, and Automated Optical Inspection (AOI) Machines. PCBWay are having 50+ new engineers on a daily basis around the world using PCBs for their work, who trust their reliable quality. They produce high-quality pink, orange, grey, and even transparent solder mask. Moreover, according to people’s needs, they can also provide Black core PCB. Check it out for a High-Quality PCB solder mask. There are some pictures below of the new colours of solder musks.
Features of PCBWay
PCB Prototyping & Manufacturing: PCBWay produces FR-4 and Aluminum boards and advanced PCBs like Rogers, HDI, and Flexible and Rigid-Flex boards, at a very reasonable price. Just check this Instant Quote to order premium PCBs for your hobby projects.
PCB Assembly: It not only offers PCB Prototyping but also offers PCB Assembly service. You can order a full PCB board with attached components by uploading your file. SMT & THT assembly starts from only 30$ including free stencil and worldwide shipping. The components can be sourced and provided by PCBWay, or by the clients themselves.
Open Source Community: It not only offers PCB Prototype & Assembly services but also gives opportunities to students for sponsorships. I think this is so great. They feature their projects on the website also.
3D Printing & CNC: It also produces Rapid Prototyping like 3D printing, CNC Machining, Sheet Metal Fabrication, and Injection Molding. The quality of the product is too premium and reliable. And also the best part is that you will receive your order within a minimum of 3 days.
PCBWay Store: More boutique gift modules are waiting for you to discover, giving your creativity wings. You can order all types of electronic equipment, components and many more with exciting offers. Go with the link and buy your needs, PCBWay Store.
Services: PCBWay offers great servicing of its products. It takes only 3 to 15 days according to the courier service to deliver your products. Also, it has a live support facility. Whenever you have any problems, you can always reach a live customer service person to respond to your emails or messages. They have the “Return and Refund” principle, for every unusable board caused by PCBWay, they will rebuild and refund the order soon.
How to Calculate Current Ratio for AC Current Measurement
If a magnetic field is enclosed around a closed loop of wire, the value of the integral is equal to the net current enclosed by the loop. The primary coil of the Current Transformer has the main wire with the current we need to measure passed through the centre of the core. The primary coil that carries the main current is said to have a single loop. The wire produces the magnetic field that drives the current on the secondary winding, which is used as the output of the CT sensor.
The current on the secondary winding is proportional to the current flowing through the centre of the core. Let’s suppose the current on the centre core is 20 amps and in the secondary coil with a 20 milliamps ratio. It means that 20 amps on the primary circuit would produce 20 milliamps on the secondary coil.
Turns Ratio = Np / Ns = Is / Ip
Np = Turns in the primary winding
Ns = Turns in the secondary winding
Ip = Current in the primary winding
Is = Current in the secondary winding
Now we need to calculate the Ns.
Let’s consider the current ratio as 20A:20mA.
Is = 20mA , Ip = 20A = 20000mA, Np = 1
Ns = (Np * Ip) / Is
Ns = (1 * 20000) / 20
So, Ns = 1000 turns
Burden Resistance for AC Current Measurement
Another important passive component is burden resistance which protects the CT sensor under open-circuit conditions. This is connected across the secondary coil of the current transformer. To avoid high voltage protection, the secondary coil or winding should always be in close circuit condition. But due to an incorrect connection of the circuit, a high voltage will be created across the secondary terminal. By using burden resistance, this type of error will be solved.
Working Principle of AC Current Measurement Circuit
Now we are going to discuss how this circuit will actually work. Firstly, connect the load to with AC mains supply and pass any one of the load’s wires (Either line or neutral but don’t pass both of them) through the middle of the CT sensor. This wire acts as the primary winding for the current transformer.
Due to the presence of AC current in the primary wire, AC voltage is induced in the secondary winding as well. Now to convert this AC voltage into DC voltage, a half-wave rectifier is used. This half-wave rectifier is in forward biased in the positive half cycle and reversed bias in the negative half cycle.
To rectify the ripples and get a smooth DC voltage, we added a capacitor at the output of the half-wave rectifier. The output voltage that is obtained from the rectifier circuit is of very less magnitude, so we use an LM358 operational amplifier with a feedback resistor.
The output of the non-inverting op-amp is:
Vout = (Rf / R1 + 1 ) Vin
Rf = feedback resistor value i.e., 10K
R1 = 1K
Vout = output voltage of LM358
Vin = applied voltage of non-inverting terminal of op-amp
So, Vout = (10 / 1 + 1 ) Vin = (11 * Vin)V
A library needs to download LiquidCrystal_I2C.
LiquidCrystal_I2C lcd(0x27, 16, 2);
readValue = analogRead(current);
Voltage = (5./1023)*readValue;
Value = Voltage/10.680;